- James Magic tube type T8 dual function which can work with specific ballast and without any ballast is an energy saving product as special replacement for traditional flourescent T8 lamps.
- Designed to operate on existing all instant start ballast,rapid start ballast and programmed start ballast and emergency fixture with input voltage of AC120-277V, AC347V.
- This magic tubes minimize labor and recycling costs.
- THD less than 20%, Power factor more than 0.90.
- Reduces energy consumption up to 40%.
- Stable lumens output for different ballast brand with different ballast factor.
- No UV emission.
- This tube can work with specific electronics ballast and also without any ballast.
- Model Name:ZY-T8-12W1200 Magic Led Tube
- Life Span:50000 Hours
- Led Chip:96 pieces of SMT 2835
- Power Factor:More than 0.90
- Efficiency: l40 lm/W
- Certificates:DLC 4.0,UL type A and UL type B,cUL,NSF,Lighting Facts,RoHs
Prepair for Installation
- Check the ballast installed in the field and make sure the ballast is in manufacturer's ballast list. If the ballast out of the list, a test must needed before mass installation.
- Loose and damaged lamp holder and socket need to be adjusted or be replaced.
"Plug" and "Play" procedure
- Turn off the power to the light fixture at the breaker panel before installation.
- Open the diffuser from the light fixture.Ensure pins are firmly seated in lampholders.
- Remove the flourescent tubes, Please dispose of these items properly as they contain mercury.
- Put led tube into the lighting fixture.
- Install the Led tube,close the diffuser.
- Turn on the power.
Please click here to download specification